CIRCUIT BREAKERpresented by: M Aamir sohail khan & sufyan saleemDept, of electrical engineering bahaudain zakariya university Multan , Pakistan : CIRCUIT BREAKERpresented by: M Aamir sohail khan & sufyan saleemDept, of electrical engineering bahaudain zakariya university Multan , Pakistan Project Advisor: : Project Advisor: ENGR. JAHANGIR AKHTAR KHAN WHAT IS A CIRCUIT BREAKER? : WHAT IS A CIRCUIT BREAKER? A circuit breaker is an equipment that breaks a circuit either manually or automatically under all conditions at no load, full load or short circuit. Slide 4: Operating Principle
Two contacts called electrode remains closed under normal operating conditions. When fault occurs on any part of the system, the trip coil of the circuit breaker get energized and contacts are separated. Slide 5: Arc Phenomenon
An arc is struck when contacts are separated. The current is thus able to continue. Thus the main duty of a circuit breaker is to distinguish the arc within the shortest possible time. Slide 6: The arc provides the low resistance path to the current and the current in the circuit remains uninterrupted. Slide 7: The arc resistance depends upon the following factors.
Degree of ionization
Length of the arc
Cross Section of the arc Slide 8: Methods of Arc Extinction
High Resistance Method
Low Resistance Method Breaker Used In 132KV Grid Station : Breaker Used In 132KV Grid Station Oil Circuit Breaker
Vacuum Circuit breaker
SF6 Circuit Breaker Bulk Oil Circuit breaker : Air cushion Bulk Oil Circuit breaker Low Oil Circuit Breaker : Low Oil Circuit Breaker Consists of two parts.
Circuit-Breaking chamber( consist of fixed and moving contact) Disadvantages Of Oil Circuit Breaker : Disadvantages Of Oil Circuit Breaker It is inflammable and there is a risk of fire.
It may form an explosive mixture with air.
It requires maintenance.
Absorbs moisture, so dielectric strength reduces.
Oil leakage problem.
Oil has to be replaced after some operations because of the carbonization of oil. Vacuum Circuit Breaker : Vacuum Circuit Breaker Vacuum is used as an arc quenching medium.
Have greatest insulating strength.
10-7 to 10-5 pressure is to be maintained.
Used in 11KV panel in control room of grid station. Vacuum Circuit Breaker : Vacuum Circuit Breaker Advantages : Advantages Compact, reliable and have longer life.
No fire hazards.
No generation of gas during and after operation.
Can interrupt any fault current.
No noise is produced while operating.
Require less power for control operation. SF6 Circuit Breaker : SF6 Circuit Breaker Sulphur Hexafluoride (SF6) gas is used as an arc quenching medium.
SF6 is an electro-negative gas.
It has strong tendency to absorb electrons.
When contact are opened in a high pressure flow of SF6 gas, arc produced.
Free electron in the arc are captured by the gas.
Which build up enough insulation strength to extinguish arc.
it is much effective for high power and high voltages services, Advantages : Advantages Simple construction, less cost.
SF6 gas is non flammable, non toxic & chemical inert gas.
Same gas is recirculated in the circuit.
Maintenance free C.B.
Ability to interrupt low and high fault current.
Excellent Arc extinction. Advantages Of SF6 Over Oil Circuit Breakers : Advantages Of SF6 Over Oil Circuit Breakers Short arcing time
Can interrupt much larger currents
Gives noiseless operation due to its closed gas circuit
No moisture problem
No risk of fire
No carbon deposits. So no tracking and insulation problems
Low maintenance cost Slide 20: THE END