logging in or signing up circuit breaker aamir.niazi Download Post to : URL : Related Presentations : Let's Connect Share Add to Flag Embed Email Send to Blogs and Networks Add to Channel Copy embed code: Embed: Flash iPad Dynamic Copy Does not support media & animations Automatically changes to Flash or non-Flash embed WordPress Embed Customize Embed URL: Copy Thumbnail: Copy The presentation is successfully added In Your Favorites. Views: 28106 Category: Education License: All Rights Reserved Like it (34) Dislike it (0) Added: July 01, 2008 This Presentation is Public Favorites: 20 Presentation Description No description available. Comments Posting comment... By: sravankingmaker (12 month(s) ago) hi sir i need dis ppt so pls send it to my mail email@example.com nd pls allow me to download dis ppt Saving..... Post Reply Close Saving..... Edit Comment Close By: avay_aol (27 month(s) ago) very goog Saving..... Post Reply Close Saving..... Edit Comment Close By: venkynani (27 month(s) ago) hi sir i need this ppt so please send my to firstname.lastname@example.org Saving..... Post Reply Close Saving..... Edit Comment Close By: rinky00 (30 month(s) ago) .i need this presentation..plzzz . Saving..... Post Reply Close Saving..... Edit Comment Close By: aamir.niazi (30 month(s) ago) thanx Saving..... Post Reply Close By: lsak (21 month(s) ago) send this ppt now plzzz Saving..... Edit Comment Close loading.... See all Premium member Presentation Transcript CIRCUIT BREAKERpresented by: M Aamir sohail khan & sufyan saleemDept, of electrical engineering bahaudain zakariya university Multan , Pakistan : CIRCUIT BREAKERpresented by: M Aamir sohail khan & sufyan saleemDept, of electrical engineering bahaudain zakariya university Multan , Pakistan Project Advisor: : Project Advisor: ENGR. JAHANGIR AKHTAR KHAN WHAT IS A CIRCUIT BREAKER? : WHAT IS A CIRCUIT BREAKER? A circuit breaker is an equipment that breaks a circuit either manually or automatically under all conditions at no load, full load or short circuit. Slide 4: Operating Principle Two contacts called electrode remains closed under normal operating conditions. When fault occurs on any part of the system, the trip coil of the circuit breaker get energized and contacts are separated. Slide 5: Arc Phenomenon An arc is struck when contacts are separated. The current is thus able to continue. Thus the main duty of a circuit breaker is to distinguish the arc within the shortest possible time. Slide 6: The arc provides the low resistance path to the current and the current in the circuit remains uninterrupted. Slide 7: The arc resistance depends upon the following factors. Degree of ionization Length of the arc Cross Section of the arc Slide 8: Methods of Arc Extinction High Resistance Method Low Resistance Method Breaker Used In 132KV Grid Station : Breaker Used In 132KV Grid Station Oil Circuit Breaker Vacuum Circuit breaker SF6 Circuit Breaker Bulk Oil Circuit breaker : Air cushion Bulk Oil Circuit breaker Low Oil Circuit Breaker : Low Oil Circuit Breaker Consists of two parts. Supporting Chamber. Circuit-Breaking chamber( consist of fixed and moving contact) Disadvantages Of Oil Circuit Breaker : Disadvantages Of Oil Circuit Breaker It is inflammable and there is a risk of fire. It may form an explosive mixture with air. It requires maintenance. Absorbs moisture, so dielectric strength reduces. Oil leakage problem. Oil has to be replaced after some operations because of the carbonization of oil. Vacuum Circuit Breaker : Vacuum Circuit Breaker Vacuum is used as an arc quenching medium. Have greatest insulating strength. 10-7 to 10-5 pressure is to be maintained. Used in 11KV panel in control room of grid station. Vacuum Circuit Breaker : Vacuum Circuit Breaker Advantages : Advantages Compact, reliable and have longer life. No fire hazards. No generation of gas during and after operation. Can interrupt any fault current. No noise is produced while operating. Require less power for control operation. SF6 Circuit Breaker : SF6 Circuit Breaker Sulphur Hexafluoride (SF6) gas is used as an arc quenching medium. SF6 is an electro-negative gas. It has strong tendency to absorb electrons. When contact are opened in a high pressure flow of SF6 gas, arc produced. Free electron in the arc are captured by the gas. Which build up enough insulation strength to extinguish arc. it is much effective for high power and high voltages services, Advantages : Advantages Simple construction, less cost. SF6 gas is non flammable, non toxic & chemical inert gas. Same gas is recirculated in the circuit. Maintenance free C.B. Ability to interrupt low and high fault current. Excellent Arc extinction. Advantages Of SF6 Over Oil Circuit Breakers : Advantages Of SF6 Over Oil Circuit Breakers Short arcing time Can interrupt much larger currents Gives noiseless operation due to its closed gas circuit No moisture problem No risk of fire No carbon deposits. So no tracking and insulation problems Low maintenance cost Slide 20: THE END You do not have the permission to view this presentation. In order to view it, please contact the author of the presentation.